Alamo, CA Heating and Air Conditioning Services
for Alamo, CA
In the Alamo area performing a furnace repair. This furnace unfortunately had a leak from the collector box and sediment trap! After replacing the collector box and sediment trap as well as adding adhesive to this leaking area, Our customer no longer has a leak!
Performing a diagnostic service on a 2018 Lennox furnace in Alamo, CA. The system is having a drainage issue causing water to build up inside the inducer motor and pressure switch, which in turn shuts the system down. The client had another company out earlier today that told him the motor needed to be replaced and that it would be over $3k to fix. I was able to get the motor running by draining it, and with some adjustments to the drains the system should be heating the home again very soon!
Performing diagnostic service on 1992 Heil furnace that is not igniting. Diagnosed failing circuit board that is intermittently sending signal to spark igniter but not able to start the system up. Repaired connections and secured wiring for temporary fix - clients are planning to replace the furnace and ductwork and add AC. They are also looking to relocate the furnace to the attic to free up closet space. Went over options and look forward to working with clients on this project! Thank you!
Furnace maintenance tuneup and clean
3x furnaces maintenance tuneup