Redwood City, CA Heating and Air Conditioning Services
Check out what our customers are saying about Certified Heating and Air Conditioning – Air Conditioning and Heating Services!
for Redwood City, CA
Great Service Brittany!
Kharla - Redwood City, CA 94061
Brittany showed up on time, she was very knowledgeable and had our furnace repaired within a short time. Our furnace is very old, when it comes time to replace our furnace I will definitely call this company again!! Thank you Britany for providing great service.
Thorough inspection, analysis, & explanations
Jeff - Redwood City, CA 94061
After doing her thorough inspection & analysis, Brittany gave us detailed descriptions of our repair and/or replacement alternatives: times, costs, warranties, etc. Cordial, professional, & responsive to questions. Couldn't ask for better.
Thorough, professional and friendly
Colleen - Redwood City, CA 94062
Brittany showed up on time and had everything needed to do the job. She explained all her findings and walked me through the problems with our furnace. Brittany reviewed all our options with me but did not pressure me into making any decisions right away. She was very friendly and professional. I would trust her to come back and service my furnace again.
Performed tune up on air conditioner, system operating upon arrival but client complains of loss in velocity of airflow. Found home just had blown insulation added and when removing filters to clean found insulation clogging return. Removed insulation and found blower leaking oil and dirty and blower capacitor below spec at 5.6 and rated for 7.5. Evaporator coil dirty and heat exchanger very weak. Outdoor unit compressor pulling high amps causing increased stress and high utility costs. Contactor burnt and pitted, cleaned outdoor unit and system is operating but disconnect in return is causing more insulation to get pulled into furnace. 32 year old system recommend upgrading
Returned to perform repairs on 2001-2002 carrier high efficiency system - replaced blower motor and wheel, thoroughly cleaned blower wheel and blower compartment, added filter, cleaned dryer vent and balanced R22 refrigerant. System is now cooling the home.
Performed a furnace tune up on an 8 years old Payne. Unit in good shape. Was installed properly. Only needed a cleaning. Client joined maintenance program to keep system in tip top shape