Certified Heating & Air Conditioning provides heater and air conditioning repair, service, installation and services in Antioch CA and surrounding areas. Check out what some of our customers are saying about Certified Heating & Air Conditioning Heating and Air Conditioning services.
for Antioch, CA
Great service. Wonderful customer service.
Kristin - Antioch, CA
Doug - Antioch, CA
Waiting for estimate
Fantastic service very professional
Vena - Antioch, CA
The technician arrived on time took his time going through our heating and air conditioning and shared some good and some not so good information but I felt that he was very honest
Performed air conditioner tune up on 20 year old Trane. Found several dirty components. Client decline repairs
Performed tune up on 18 year old York air conditioner. Unit has no major failure. It is however very inefficient. It’s using a lot of energy to run and because it is not cooling the house effectively it is running longer. Did what I could to make system run better but client declined repairs so options were limited.
Performing AC tune up service on 1991 Rheem condenser. Client felt that system was unable to keep the home cool during the brutal summer heat waves, on top of that his PG&E bills skyrocket when the system is in use. Went through system, cleaned thoroughly, and inspected and tested all electrical and safety components. Set up appointment to go over solar system options along with options on equipment that will work directly with the solar panels to drastically reduce their utility bills.
Performing AC precision tune up on 1992 Payne condenser in the Williamson Ranch neighborhood of Antioch. Checked refrigerant levels, R22, inspected and tested all the electrical and safety components and made recommendations to make system better. Gave an estimate to replace the system and add an AirScrubber Plus to clean ducts and make breathing air as healthy as possible. Looking forward to working with clients to keep them comfortable in their beautiful home. Thank you for choosing Certified!
Performed tune up on 16 year old Goodman R22 air conditioning system. Replaced filter, cleaned outdoor unit. Checked capacitors, contactor, electrical connections, refrigerant levels and amperage draw on compressor, condenser fan motor and blower. Indoor air conditioner coil rusty and dirty lowering efficiency and adding stress to system, condensate pan has hole which caused water damage to ceiling. Compressor is failing and is very loud, low on refrigerant. Furnace blower leaking oil and dirty
Performing AC diagnostic service on 1985 Day & Night condenser. Discovered that the reason the system is not able to cool the home is because the R-22 refrigerant level is extremely low, causing the evaporator coil to freeze over. Made recommendations for potential repairs and discussed replacement options.
Air conditioner maintenance on 17 year old carrier R22 system. Checked filters, cleaned outdoor unit, checked capacitor, contactor, electrical connections and refrigerant levels. Checked amperage draw on compressor and condenser fan motor. Inspected evaporator coil for rust and debris, as well as furnace blower assembly for dirt and to see if it is leaking oil or grease. Compressor has a bearing that is starting to fail causing a very loud noise on start up
Air conditioner tune up on 18 year old Goodman R22 air conditioner. Compressor pulling high amps, contactor burnt and pitted. Due to age, efficiency, condition and cost of repairs client looking at replacement options for a system that’s more efficient and reliable
Going over replacement options for clients to ensure they have a functioning air conditioner to get them through the hot Antioch summers. Clients became maintenance members and a new system is being installed very soon. Clients took advantage of our excellent 18 months 0 interest program and we are fully confident that they will be extremely happy with their new heating and air system! Thank you for choosing Certified!
Tune up in Antioch on both the furnace and the ac. Need to get client ready for this heat that will soon be here.
Certified member maintenance 28 point rejuvenation
Furnace tune up.