Certified Heating & Air Conditioning provides heater and air conditioning repair, service, installation and services in Oakley CA and surrounding areas. Check out what some of our customers are saying about Certified Heating & Air Conditioning Heating and Air Conditioning services.
for Oakley, CA
Carolw - Oakley, CA
Yvonne was and excellent representative of Certified Heating and Air Conditioning ! Very polite and she knew what she was doing. Great tune up! Thanks
Steven - Oakley, CA
Rosemary - Oakley, CA
We were very happy with our tech and she seemed to know her job and was very helpful with any questions we had, and now our air is working very well, thank you
Mark - Oakley, CA
Mr Damico - Oakley, CA
It's been freezing out and of course my heater decided to take a dump. My house has been 55 degrees and it's been miserable. Bryan came out and replaced the circuit and now I have heat again. Thank you Bryan and Certified Heating and Air Conditioning!
Sergio - Oakley, CA
Etene - Oakley, CA
Competitive and custom professional craftsmanship! It's getting cold and make sure your prepared by calling CERTIFIED HEATING AND AI CONDITIONING
Performed diagnostic on air conditioner found system not coming on at all found thermostat had been replaced but jumper for heating and cooling was missing. Installed jumper to get furnace operating. Found condenser fan motor failed and compressor amperage high due to fan not working properly. Blower motor leaking oil and using more power than manufacturer allows, blower capacitor below spec. Blower and evaporator coil dirty.
Performing system tune up on 1986 carrier furnace and 2000 carrier condenser. Cleaned system out, checked all safety and electrical components. Checked refrigerant levels, cleaned condenser coil thoroughly. Made recommendations for minor repairs to keep system running for as long as possible. Clients are currently in the process of moving out of state and we wish them the best of luck on their new adventure.
Tune up on Payne air conditioner, cleaned outdoor unit, checked capacitor, contactor, electrical connections, refrigerant levels and amperage draw on compressor, condenser fan motor and blower. Outdoor unit not matched to indoor unit causing high electrical consumption and improper cooling.
Performing precision tune up on 2007 Carrier condenser. Family was having trouble cooling home below 80 degrees during the heat wave last summer. Discovered airflow restrictions and corrected them, added R410a refrigerant for proper balance and increase the temperature split from 9 degrees to almost 20! System is now effectively cooling the home and clients became annual maintenance members to continue having system maintenance performed by the best technicians in the industry.
Estimate to replace existing system.