Certified Heating & Air Conditioning provides heater and air conditioning repair, service, installation and services in Pittsburg CA and surrounding areas. Check out what some of our customers are saying about Certified Heating & Air Conditioning Heating and Air Conditioning services.
for Pittsburg, CA
Steven - Pittsburg, CA
Great service, awesome price!
Richard - Pittsburg, CA
Trustworthy and pretty darn quick repair job.
Dean - Pittsburg, CA
My experience with certified was fantastic the service technician Britney Britland what's prompt polite and very informative she determined that the problem was the ducting and she called our landlord and spoke with him to explain exactly what was wrong overall I was very satisfied with certified
Perform diagnostic when you’re old air conditioner. Unit not cooling the home. Found a dirty filter, recommend client to clean every 30 to 60 days. And added refrigerant. Unit running well client joined maintenance program
Performed diagnostic on system neither furnace nor air conditioner operating upon arrival. Found low voltage fuse popped due to short in low voltage wiring, located and fixed short and tested system operating properly at this time. 2800sqf home three ton air conditioner, four ton furnace and two tons of ductwork per zone. No ssu switch, no sealtight for low voltage wiring at condenser, no dedicated transformer for zoning.
Performing AC tune up service on 1997 Rheem condenser. Checked refrigerant levels, inspected and tested electrical and safety components, made recommendations for repairs and replacement options. Thoroughly cleaned condenser coil to allow more airflow to keep compressor cool.
Performed air conditioner tune up on 17 year old Trane. Everything checked out well, cooling properly. Some minor issues regarding efficiency. Client would like to upgrade to a more efficient system, currently has a 12 SEER and would like a 16-18 SEER.
Performed diagnostic on 17 year old York air conditioner. Unit had a failed capacitor and a tripped breaker. Reset breaker, replaced faulty wire, and dual capacitor. Unit runs but is likely to have another breakdown due to high energy consumption on hot days.
Ac diagnostic condenser not running and not cooling home replaced part client satisfied
Ac tune up with a safety inspection on furnace.
Fixing a broken furnace. Sure is cold out.